ISO (E). PDF disclaimer. This PDF file may contain embedded typefaces. In accordance with Adobe’s licensing policy, this file may. IS/ISO – – Reciprocating Internal Combustion Engine Driven Alternating Current Generating Sets, Part 6: Test Methods. Thumbnails Document . Find the most up-to-date version of ISO at Engineering
|Published (Last):||6 December 2004|
|PDF File Size:||8.85 Mb|
|ePub File Size:||6.40 Mb|
|Price:||Free* [*Free Regsitration Required]|
For some specific applications e. Accept and continue Learn more about the cookies we use and how to iwo your settings. It applies to alternating current a.
Generating sets lEC Standards Subscriptions from ANSI provides a money-saving, multi-user solution for accessing standards. If the acceptance test is interrupted by major faults which necessitate the repair or replacement of important components, the acceptance test shall be repeated either wholly or in part once the interruption has been rectified.
Reciprocating internal combustion engine driven alternating current generating sets — 8258-6 8: The groups for the checks and measurements are summarized in Table 3. Reciprocating internal combustion engine driven alternating current generating sets — Part 6: If the test is carried iiso at the manufacturer’s works, the tolerances shown in 5.
Need more than one copy? Reciprocating internal combustion engine driven alternating current generating sets — Part 4: The validation of further requirements, the performance of additional measurements or the provision of further tests which go beyond the requirements of 6.
If the document is revised or amended, you will be notified by email. A test report shall iwo prepared in accordance with the requirements of 5.
Reciprocating internal combustion engine driven alternating current generating sets — Part 7: Your basket is empty. Methods for determining losses and efficiency of rotating electrical machinery from tests excluding machines for traction vehicles For the purpose of deciding whether a particular requirement of this standard is complied with, the final value, observed or calculated, expressing the result of a test or analysis, shall be rounded off in jso with IS 2: Measurement and evaluation of mechanical vibrations.
The responsibilities of the customer and the manufacturer’s agent shall be agreed before starting the acceptance test.
Click to learn more. For undated references, the latest edition of the referenced document including any amendments applies.
This Indian Standard has been developed from Doc No.: NOTE It is not possible to measure voltage and frequency without electrical excitation equipment being connected. You can download and open this file to your own computer but DRM prevents opening this file on another computer, including a networked server. Emergency power supply to safety services. This does not preclude the free use, in course of imple- menting the standard, of necessary details, such as symbols and sizes, type or grade designations.
Reciprocating internal combustion engine driven alternating current generating sets – Part: Optionally, if this is not possible because of the test equipment used, this test may be performed at a power factor of unity.
The provisions of ISO The cost of a complete or partial repetition or extension of the agreed acceptance test programme shall be borne by the party responsible for the repetition or extension. The corresponding Indian Standards which are to be substituted in their respective places are listed below along with their degree of equivalence for the editions indicated: Measuring transformers and transducers should be of a corresponding accuracy class.
BS ISO 8528-6:2005
If the requirements of the tests specified in Clause 6 are changed during the acceptance test, an appropriate agreement shall be made. The test equipment used shall be such that the measurements and checks agreed for the acceptance test can be verified within the agreed accuracy limits.
Classification of degree of protection provided by enclosures for rotating oso lEC Again there may be more recent versions of the document. This website is best viewed with browser version of up to Microsoft Internet Explorer 8 or Firefox 3.